An actuator is a device used to open, close, or control valves. The most commonly used types are electrical, hydraulic, and pneumatic. For high torque applications, electro-hydraulic actuators may be utilitzed. Actuators are mounted to the valves by a linkage.
Actuators may be quarter turn or multi-turn. They might fail in place, fail open or closed or continue to run, depending on the set up. Actuators are sized depending on their application. butterfly valves, for example, require the highest torque immediately after opening and the torque requirements depend on the orientation of the valve.
types of actuators
Manual actuators are knobs, cranks, gear operators or hand levers. Movement may be quarter turn or multi-turn, depending on the required actuation.
During design and construction of a project, valves or actuators may end up in hard to reach locations. Chain wheels are used to access these valve from a floor location in a safe operating manner.
Chain Wheel Operator Photos
Pneumatic actuators use compressed air controlled by a separate solenoid valve, while motor actuators use an electric gear motor. Actuators may be used when valves are remotely located (such as on pipelines), located in hazardous areas, and when manual operation would be time consuming (like with large valves).
Pneumatic Actuators will typically have one of the following characteristics
- Air to Open - An actuator installed in this configuration requires air to open. If the actuator is a rack and pinion actuator and is single acting, it must have a spring to force the valve closed when there is no air in the actuator. Air to open type actuators require air pressure and some known volume to open the valve. Actuators that require air to open are typically denoted as "fail closed".
- Air to Close - Air to Close is of a different configuration than the ATO type actuator described above. Air to Close means that constant pressure must be held on the acutator to keep the valve closed. If air pressure is lost the actuator will automatically open. Actuators that require air to close are typically denoted as "fail open".
- ACTR - Actuator